02 Nov 2018 - Peter
Recently, a PLC controlled heating system failed, causing the product to go over temperature resulting in substantial consequential losses.
An engineer dispatched to deal with the problem found that the CPU was not reading inputs, and replaced the input module to no effect. He condemned the system and recommended replacement in its entirety.
The customer, not happy with the proposed cost and delay to operations, took a second opinion.
A diagnostic scan revealed the root cause – incompatibility between the new input module and older CPU firmware. The firmware was upgraded, the plant set to work and production was soon back to normal.
Had preventative maintenance been implemented keeping the CPU firmware up-to-date, the new input module would have worked when installed and loss of production would have been minimised.
Is an audit of your automation overdue? Op-tec is here to help
Let Richard serve you regular breakfast emails. Useful information for those lookng to make improvements to their operations, from project justification to reminders about the importance of security and disaster recovery.
Knowledge and insights into your inbox.
Have one of our experienced engineers visit your site to review your existing operations, discuss how we can help and provide you with a prioritised action plan describing how to improve your operations.
A free, no obligation service.
Need assistance right away? We have expertise with a wide variety of automation equipment and software. So if you're looking for help get in touch and we'll do everything we can.
We offer support agreements so there's always someone on the end of the line.
More from Peter